Requirements of Bed material,Charcoal & Diesel. Bed material Maximum Particle size Bulk density Chemical composition MM TO The start up of fluidised bed combustion boilers has always been a subject of the most process of raising bed temperature above °C. In the process of. boilers/heaters is the concept of Fluidised Bed Combustion (FBC). A descriptive feature for Start up/ Firing Procedure for AFBC boiler/heater bed. Initially.
|Published (Last):||2 May 2013|
|PDF File Size:||18.25 Mb|
|ePub File Size:||16.16 Mb|
|Price:||Free* [*Free Regsitration Required]|
Check the bed material and fludisation study is being done. Feed pump and drives.
Valves on feed line connecting to feed pumps operation. Feed control valve and its bypass valve. C and start the ash handling system. Boiler Installation – Afbc Documents. Published on Oct View 3. Fuel feeders and controllers. A fixed quantity of diesel wetted Charcoal 40 Kgs is spread uniformly over the compartment. Add gas plenum pressure P2 Furnace draught to P1. Afbc Boiler Operation Manual – snowman-ro. Ensure all equipment trial to be taken.
Bed material to be filled and level of defluidised bed should be MM of WC. Cfbc Boiler s,ebooks and documents of cfbc boiler operation manual thermax – afbc boilers, Bed super heater drains. Drain valves of water level gauge. Ensure all access doors are closed.
THERMAL POWER PLANT A-Z: boiler light up detailed
Check for dry fuel MM is available in bunker and gates below bunker are open and fuel is available at feeder inlet. All interlocks to be cross checked. Initally the top bed temperature will raise and at the time of mixing temperature drops and bottom temperature raises at the time of mixing. Cethar Afbc Boiler Manual – dire searching for a ebook Cethar afbc boiler manual in Measure air box pressure P1 MM of wc 3.
Ensure the deaerator water level as normal. Main steam stop and pilot valve.
Ensure feed water flow through economiser at the time of light up to avoid steaming of economiser. Cfbc boiler operation procedure?
Afbc Boiler Light Up Procedure
Shiatsu Massage Manual Afbc boiler boiler, The When the bed temperatures reaches Deg C start the drag chain coal feeder. Light up all the four burners. Set the air flow to MM of wc P. Boiler Manual For Cfbc – boiler operation procedure? Inspect the boiler before start and check the following 1.
Valves before ligh after feed control valve in feed line. Start up vent valve. Check the following valves are kept in open condition. Bed material Maximum Particle size Bulk density Chemical composition: Drum and main line vent. Boiler light up procedure A fixed quantity of dry charcoal Kgs i.
Afbc Boiler Light Up Procedure
Afbc Boiler Operation Manual – boiler operation manual at Inspect the boiler before start and check Manual on Boiler Tube Bhel steam generators products afbc boilers Tags: The air flow at which fludisation starts is noted and will be maintained at the time of mixing.
Keep the PA lines clear and take trial run of feeder of first compartment. Ensure all foreign materials are removed from furnance and pressure parts. Close the bed superheater drains.
CFBC boiler operation procedure? Start the FD fan and maintain bed pressure mmwc. Check the following equipments for adequate lubrication. Turn off the oil burners and remove from furnace. Inspect the boiler before start and check Manual on Boiler Tube Fluidized bed combustion – wikipedia, the free encyclopedia Fluidized bed combustion FBC is a combustion technology used to burn solid fuels.
Afbc Boiler Operation Manual – ante-annum. Once fludisation study is completed boiler is ready for light up. Ensure all personel were cleared. After stabilisation of bed temperatures stop the burners and LDO pumps.
Maintain drum level at normal recommended level. C and stable the boiler. The pressure drop across bed is obtained for various air flow.